• Product Code: MS04
INSTALLATION INSTRUCTIONS – FF170 Hand Held Nozzle Grade Foam
Cutting knife, tape for masking of adjacent areas. Unstable areas may need to be clamped or secured during curing.
- Always carry out a test to confirm compatibility prior to use.
- Protect floor coverings with paper or a plastic film.
- The surfaces must be dry, solid, stable and capable of carrying the load of the panels to be installed.
- Remove all loose particles, dust and grease.
- A speedier cure can be attained by moistening the substrates if needed.
- Shake the canister vigorously at least 20 times. Leaving the cap on the can, screw the nozzle firmly into the connector on the top of the trigger.
- Remove safety catch and pull the trigger to activate can. Fill approximately half of the required depth of the cavity because the foam will expand.
- On horizontal surfaces always work away from the exuding bead and work upwards on all vertical surfaces.
- The foam is firmly set in approximately 1 hour (depending on temperature and humidity) when any excess can be trimmed with a sharp blade.
Remove excess foam immediately with illbruck PU foam cleaner or acetone. Ensure surface is solvent resistant before cleaning. Cured foam can only be removed mechanically.
Store between +5°C and +25°C in dry conditions.
9 months when stored in its original unopened containers.
Health & Safety Precautions
Safety data sheet must be read and understood before use